Improve your steam efficiency with Miyawaki Steam TrapExplore our range of steam traps designed to optimize your system’s performance, reduce energy costs, and ensure a seamless operation.
a. Thermodynamic Steam Trap
Operates using a disc mechanism, providing reliable condensate removal and contributing to enhanced system efficiency.
Simple operation and low cost
b. Thermostatic Steam Trap
Utilizes temperature-sensitive elements to modulate condensate discharge, ensuring precise control in various steam system conditions.
Good durability for high pressure applications and superheated steam
c. Float Trap
Employs a float mechanism to open and close, efficiently draining condensate and preventing steam loss.
Good for large condensate loads such as heat exchanger applications
d. Inverted Bucket Trap
Features an inverted bucket mechanism that opens and closes with condensate, providing efficient drainage and reliability.
Good for medium condensate loads
Sizing & Selection
|< 1,6 MPa
|GC1, D, S, ES
|< 2,1 MPa
|< 6,4 MPa
|S61, S62, ESH
|< 19,6 MPa
|TB71, TB72, TB81, TB82
|Steam Tracer Lines
|D, ES, S
|Copper Tracing (Instrument Tracing)
|G, S, ER
|ES, G, S
|ES, ER, D
|ES, D, S
|ES, D, S
|ES, D, S
|Process Boiling Pans
|Jacketes Boiling Pans
|G, ES, S
|Heating & Air
|Air Conditioning Units
The purpose of sizing is to ensure that the discharge capacity can meet the requirements. First of all the steam flow rate must be known. After applying a safety factor of around 2 to 3 times, the required capacity of the steam trap is known.
Based on the differential pressure (difference inlet and outlet pressure of the steam trap), the maximum capacity of the selected steam trap can be known. The maximum capacity of the steam trap must be higher than the required capacity.
Where should I install a steam trap?
Ideally, a steam trap should be installed every 30m to 50m of steam piping. Steam traps should be installed at the lowest point. Not only is this better for good discharge of condensate, it also facilitates the maintenance of the steam traps.
Avoid group trapping if possible. Always use individual trapping.
Maintenance through Steam Trap Survey
An efficient trap wastes less energy. In addition, it also maintains clean and dry steam.
Under the proper conditions, a steam trap is expected to last around 3 – 5 years. However it can fail prematurely due to:
- Pipe debris such as pipe rust
- Steam cuts especially at high pressures
- Improper orientation during installation
If a failed steam trap is not replaced, it could lead to issues like water hammer or the process cannot achieve the required temperature.
The most common issue is leakage of the steam trap. When this happens steam can be seen to be flashing from the steam trap. There could also be small leaks which can only be detected using an ultrasonic vibration detector or thermal imaging.
Besides being a health hazard, even a small leak could potentially lead to thousands of dollars in energy loss over time. For example, if we take a thermodynamic steam trap at 3 bar steam, the financial loss per year due to leaking steam could look like this:
These calculations are for one small steam trap. In a large refinery, the number of steam traps could number in the thousands. The financial loss due to leakage of steam has a huge impact on costs and the environment.
Plugged / Choked Traps
The trap may fail to discharge condensate properly as the orifice could be choked. Dirt, pipe scale, rust, packing and joint material or debris can cause these blockages. When this happens, the user may observe that the temperature cannot achieve process requirements. In serious cases, the condensate collects at the bottom of the pipe which can result in waterhammer.
Steam Trap Inspection Survey
Techmatic performs scheduled steam trap survey to check all the steam traps periodically and ensure that all traps are in proper working conditions. We use the ultrasonic vibration, thermal imaging and stethoscope methods to check for leaks. Based on this data, the steam loss can be calculated using a software.
If found to be faulty, the trap can be replaced or serviced.